Published at Monday, March 25th, 2019 - 14:26:53 PM. wiring. By Leona Coste.
In the example shown, line 5 has the numbers 5 and 11 printed to the right of the line. This means that the load (HR) controls a set of contacts in lines 5 and 11. The contact in line 5 is normally open and the contact in line 11 is normally closed. Many times there are also small numbers printed next to each of the electrical components on the diagram. In our example, we have colored these numbers blue. These smaller numbers represent the manufacturer’s numbers stamped on the actual electrical component. For example, the compressor overload OL2 has the numbers 3 and 4 printed next to it. This means that the wiring shown on the diagram will be physically connected to terminals 3 and 4 on the actual overload. This allows a technician to more easily locate an exact point in the wiring of the system. Lastly, some diagrams will also have a circled number shown next to a line on the diagram. These circled numbers are used to identify the actual wires used on the system.
Bob and Tim are at a job where a technician from another company could not figure out the electrical, so he just put the panel back on the electrical compartment and left the job. It is a heat pump and the compressor wiring is all loose. They need to figure out how to wire it back and find out the problem. The homeowner said the original call to the other service company was because of ice build up on the outdoor coil. Bob and Tim talked to the homeowner and explained that because the weather was cold and damp, ice buildup was expected on any heat pump in this kind of weather, but they would check the unit and see what was going on. The heat pump compressor was not running and the home was being heated with the auxiliary heat, so the first order of business was to get the heat pump operating. They went outside and noticed the ice had melted from the outdoor unit due to an above freezing day. The compressor was not running; however, the fan was running. They looked at the compressor and discovered the wires to the compressor were all disconnected, and the ends were taped to make them safe. “
Any content, trademark’s, or other material that might be found on the Eventionline website that is not Eventionline’s property remains the copyright of its respective owner/s. In no way does Eventionline claim ownership or responsibility for such items, and you should seek legal consent for any use of such materials from its owner.