Published at Monday, March 25th, 2019 - 02:15:52 AM. wiring. By Odile Cohen.
The largest reading was from 1 to 3, and would be the reading through both windings so that would be from 1 through common to 3. This tells you that the 2 terminal is the common terminal. “You have identified the “C” the common terminal as the number 2 terminal,” Bob explained. ”Now we know from process of deduction what the other 2 terminals are. The shortest winding with the least resistance is the run winding so terminal 2 to terminal 1 is the smallest resistance making the 1 terminal the “R” run terminal. The only terminal we have left is the “3” terminal and that makes it the start terminal. You can now take the red wire and put it on the run terminal, the white wire on the common terminal and the black wire on the start terminal. “
Being able to efficiently interpret ladder (line) diagrams is an important part of electrically troubleshooting many HVACR systems. These diagrams are drawn in such a format that it is quite easy to understand the electrical configuration of the system. The ease in reading these diagrams is accomplished by drawing each load and any switches that control that load on a separate horizontal line. For example, if a load is not energized when it should, a technician should be able to easily identify which switch or switches control that load and then start to troubleshoot the cause. Ladder diagrams are also drawn with other helpful identifiers to aid a technician in electrically troubleshooting a system.
Any content, trademark’s, or other material that might be found on the Eventionline website that is not Eventionline’s property remains the copyright of its respective owner/s. In no way does Eventionline claim ownership or responsibility for such items, and you should seek legal consent for any use of such materials from its owner.